About this building
The Cabinet Office’s headquarters building is located at 70 Whitehall, adjacent to Downing Street and a short walk from the Palace of Westminster. The Grade 1 listed building stands on the site of the old Whitehall Palace and is composed of a number of buildings constructed at different periods of time but now joined together as one.
Our energy use
This graph allows everyone to access a range of data from our offices at 70 Whitehall. It’s generated in real-time from data taken every 5 seconds from the on-site meters.
Our water use
This graph shows our water consumption at 70 Whitehall in real time. On the graph this is expressed in litres per hour (L/h).
Display Energy Certificate
Since 9 January 2013 public buildings in the UK over 500m2 have been required to display a Display Energy Certificate (DEC) prominently at all times. Display Energy Certificates were introduced by the Government in response to the EU Energy Performance of Buildings Directive which all EU member states were required to implement by January 2009.
DECs are designed to promote the improvement of the energy performance of buildings. They are based upon the actual energy performance of a building and increase transparency about the energy efficiency of public buildings. DECs use a scale from A to G with A being the most efficient and G the least. The Display Energy Certificate for 70 Whitehall is available here or by clicking the plaque on the right.
Study our data
70 Whitehall's historical resource use is available in these CSV files. We are deciding which other formats to provide data in, so if you would like to use the data for a purpose that requires another kind of file or feed, then let us know, and we'll see what we can do!
Frequently asked questions
How do you calculate the CO2e emissions from a unit of energy used?
Energy retailers and the government produce conversion factors that describe the typical carbon impact of different energy sources. These allow us to take the energy uses (in their respective units), and calculate the approximate carbon dioxide emissions, normally measured in kilograms of carbon dioxide equivalents (kgCO2e). Defra's UK conversion factors may be found at Defra's 2011 Guidelines.
Why is there no scale on the small real time graph?
We made a small, simple real time display graph (we call it a 'teaser') so that organisations can communicate about real-time energy use on their homepages. The intention of the teaser is to present very simple, somewhat intriguing information that attracts browsing users to the profile page (this page!). It has to work in a very small area, and it can't support detailed enquiry.
The building profile page where you are now is where the real information lives. This is where we provide much more detail for those who have the time and inclination to learn more.
What do the colours on the graph mean?
The colours in the graph show approximately how the current level of usage would lead to a given Operational Rating – as set out on a Display Energy Certificate (DEC) – if the performance for a given moment carried on for an entire year. This goes from dark green for ‘A’ to red for ‘G’. We calibrate this using input data used for generating the building’s DEC, together with information relating to 'normal' buildings of its type. If we do not have data for all of the utilities noted in the DEC then the graph will appear in greyscale, to indicate that the usage displayed on the graph is not representative of the full energy use of this building.
Why are you using these units and what do they mean?
We provide three different measures of the energy used: the amount of energy, its monetary cost, and the carbon impact of the energy used.
Energy use is measured in kilowatt hours (kWh), which are the standard units of a home energy bill (1kWh is the amount of electricity used by ten 100W light bulbs in one hour).
For electricity this number represents the amount of energy that flows into a building through the meter, and excludes distribution losses. For gas it is the amount of energy that is theoretically available by burning all the gas in an imaginary burner. For district heating it reflects a flow of temperature into the building over time (after the heat produced by burning the fuel has been transported to the meter, which involves other losses). So these numbers, while all being measured in kWh, mean very different things. This is one reason that we prefer to use 'units per hour' when combining them. In some ways it would be better not to combine them at all, because it implies that the measures are comparable. This is a global challenge though, and conventions have become established around combining kWh. So we'll have to fix it another day.
Monetary cost is calculated using the costs per 'unit' for each utility in every building. The figures used are noted below in the Notes section.
The carbon impact is measured in kg of CO2e (the e stands for equivalent) which takes other climate-affecting gasses into account besides carbon dioxide.
How much does this organisation pay for its energy?
Prices come from the latest energy bills for Cabinet Office, which are noted below in the Notes section. These are of course subject to change, and will be updated by the organisations themselves as tariffs are revised.
Can you show data from the transport emissions of this organisation/ building?
Data of CO2e emissions created by transport used by organisations is very interesting and powerful data to show here. We are working on ways to display and reduce the transport impacts of different organisations, and you will see some of the products of this work on these pages very soon.
Carbon conversion factors of grid electricity and district heating are based on Defra’s 2011 guidance. The factors in use are 0.2433 per kWh for district heating and 0.52462 per kWh for electricity.
Prices come from the latest energy bills, which for district heating average out at 2.90p per unit (please note that we currently are using the net price as no bills for this year are available yet) and for electricity average out at 12.03p per unit.
As far as the widget is concerned, there are 12 distinct 5-second periods in a minute. The real-time data is for the five second period just ended, which means that sometimes the widget could display values that are nearly 10 seconds old.
Because we have used the pulse-outputs of electrical and gas meters there are certain assumptions we need to make in order to generate a real-time value. The pulses from the meters actually signify a volume of gas or an amount of energy, and we need to determine a flow of gas or electrical power from the pulses. Since at any given moment you are always between one pulse and the next, you have to guess, to a certain extent, when the next pulse will come in order to estimate the actual flow or power. The accuracy of the guess depends on how close together the pulses are, so at busy times you hardly need to guess at all. The pulses from the main electricity meter come every 100 watt-hours, which is enough to let us overcome the issue by counting the number of pulses in a five second period and applying a calculation to smooth successive readings into a rate, even at night. The main gas meter pulses once for each cubic metre consumed, which for properly variable loads could leave us guessing for quite a while before the next pulse comes. We use an ‘exponential moving average’ calculation to generate the real-time value, which allows us to display a value that is as close-to-right as possible; the values go up in time with increases in actual use, but lag behind sudden reductions. The downside of this is that if you added up all the real-time values that the teaser shows every five seconds, over time it would be shown to over-report slightly. This inaccuracy in the real-time data is strongest when high gas use drops quickly (as when the main boilers shut down, which happens several times a day). This distortion in the real-time data does not introduce any inaccuracies into the archive data, and we will report on the exact degree of error introduced if there is interest in this.
The spreadsheet files available from the 'Study our data' section for 70 Whitehall were under-reporting electricity for a time due to an error, the impact of which was that one electricity meter out of the four onsite was not included in the CSV values. This was detected in routine quality assurance and has now been corrected. Please note that this error only affected the CSV downloads, not the graph and interactive values, which have correctly represented all meters throughout. Please accept our apologies for any inconvenience.